transformers” was submitted to the IEC-CENELEC parallel vote and approved The text of the International Standard IEC was. This part of IEC applies to on-load tap-changers of both resistor and reactor types, deenergized tap-changers, and their motor-drive mechanisms. accordance with IEC for use in conjunction with the tapped IEC , Tap-changers – Part 1: Performance requirements and test methods.
|Published (Last):||9 October 2015|
|PDF File Size:||2.88 Mb|
|ePub File Size:||15.68 Mb|
|Price:||Free* [*Free Regsitration Required]|
Accept and continue Learn more about the cookies we use and how to change your settings. Click to learn more.
BS EN 60214-1:2014
The following test report forms are related: Selector switches, Oil-immersed transformers, Electric reactors, Mechanical testing, Switches, Power transformers, Performance testing, Resistors, Electrical transmission systems, Electrical testing, Induction-voltage regulators, Tap-changing equipment.
This second edition cancels and replaces the first edition published in This edition constitutes a technical revision. Find Similar Items This product falls into the following categories.
Search all 60124-1 by. You may experience issues viewing this site in Internet Explorer 9, 10 or This website is best viewed with browser version of up to Microsoft Internet Explorer 8 or Firefox 3.
We accept all major credit cards American Express, Mastercard and VisaPayPal and bank transfers as form of payment. This part of IEC applies to power and distribution transformers of all types and also to reactors.
This edition includes the following significant technical changes with respect to the previous edition: Learn more about the cookies we use and how to change your settings. TC 14 – Power transformers rss.
Please download Chrome or Firefox or view our browser tips. Worldwide Standards We can source any standard from anywhere in the world. You may find similar items within these categories by selecting from the choices below:. Performance requirements and test methods Status: It applies mainly to tap-changers with arcing contacts but may also be used for arcing-free on-load tap-changers such as electronic switching insofar as conditions are applicable.
Preview Abstract IEC It applies mainly to tap-changers immersed in mineral insulating oil according to IEC but may also be used for tap-changers with air or gas insulation or immersed in other insulating liquids insofar as conditions are applicable.
IEC | IEC Webstore
Do you iwc a multi-user copy? It does not apply to transformers and reactors mounted on railway rolling stock. Related publications IEC